# Number of loaded objects in backfill

The number of loaded cables in the backfill area is individually calculated for every system as the total losses in the backfill area divided by the losses in that specific system. Hence, $N_b$ is not necessarily an integer number and can be different for every system in the backfill area.

Symbol
$N_{b}$
Used in
$T_{4db}$