# Resistance of conductor

Note: The parameter $R_{cDC}$ does not have an entry in the documentation.

Symbol
$R_{c}$
Unit
$\Omega$/m
Formulae
 $R_{co} \left(\alpha_{c} \left(\theta_{c} - 20\right) + 1\right)$ DC resistance of conductor at operating temperature ($R_{cDC}$) $R_{cDC} \left(y_{p} + y_{s} + 1\right)$ AC resistance of cable conductor at operating temperature $R_{cDC} \left(y_{c} + 1\right)$ AC resistance of GIL conductor at operating temperature
Related
$\alpha_{c}$
$\theta_{c}$
Used in
$B$
$\Delta W_{0}$
$I_{c}$
$V_{drop}$
Voltage drop [V/A/km]
$W_{c}$
$W_{h}$
$Z_{pos}$