For calculation of the cyclic and emergency current rating of cables acc. IEC 60853, the multi-core cable is replaced by an equivalent single-core construction dissipating the same total conductor losses. The space between the equivalent single-core conductor and the sheath is considered to be completely occuied by insulation (for oil-filled cables, this space is filled partly by the total volume of oil in the ducts and the remainder is oil-impregnated paper).

Symbol
$T_{\mathrm{1t}}$
Unit
K.m/W
Formulae
$\frac{\rho_{\mathrm{i}}}{2 \pi} \ln{\left (1 + \frac{2 t_{\mathrm{1t}}}{d_{\mathrm{ct}}} \right )}$
Related
$d_{\mathrm{ct}}$
$\pi$
$\rho_{\mathrm{i}}$
$t_{\mathrm{1t}}$
Used in
$Q_{\mathrm{B_{\mathrm{i}}}}$
$Q_{\mathrm{B_{\mathrm{s}}}}$
$T_{\mathrm{A}}$
$T_{\mathrm{tot}}$