Cableizer is a software for the design of power cables and for ampacity calculations based on IEC 60287 and Neher McGrath plus additional methods based on new publications.
Being web-based you can work on Windows or Mac and on-site using your laptop, tablet or even your smartphone. All you need is a current browser and a run-of-the-mill internet connection, and the amount of data being transmitted is very limited.
You access your account with login and password. Create and store as many cables and arrangements as you like free of charge. When you need to make ampacity calculations for a project, you simply order a monthly subscription for a fair price. After placing the order, calculation is immediately possible without delay. We check your commercial data and send you an invoice which can be paid in EUR, USD or CHF.
Once the subscription runs out, only calculation is blocked and no data is lost - forever!
Cyclic loading with daily, weekly, and yearly load factors (Aug 16 2016)
Using the Neher McGrath method for the calculation of the rating of buried cables under cyclic loading conditions allows for a daily, weekly, and yearly load factor in the same calculation.
Variation of spacing between sheath bonding points (Jul 03 2016)
For single-core cable circuits with sheaths solidly bonded at both ends and possibly at intermediate points, the circulating currents and the resulting losses increase as the spacing increases, and it is advisable to use as close a spacing as possible. The optimum spacing is achieved by considering both losses and mutual heating between cables.
Phase splitting (Jun 26 2016)
Phase splitting can be used to drastically reduce the magnetic fields of buried power cables. Also, the conductor cross-section can be less than half because the current is only half per split system and it can give a partial redundancy of about 60% or even more in case of a cable failure on one split system.